Already have an account? Get multiple benefits of using own account!
Login in your account..!
Don't have an account? Create your account in less than a minutes,
Forgot password? how can I recover my password now!
Enter right registered email to receive password!
Connection of Shunt Capacitors at Distribution Transformer
Provision of capacitors at load point is found to be hard in practice because of the additional investments needed. It has also been experienced in which the LT motive power consumers do not ensure the working of capacitors even if these are given at the time of release of connections. The agricultural consumers are not keen to improve the power factor of their motors, as they are not benefited because of flat rate tariff. Further, the consumers do not have requisite knowledge and skill to decide the level of compensation and check the availability.
Although planning the distribution systems, such local practical problems could be taken care of through the power utilities by giving LT capacitors on distribution transformers. Switched or fixed capacitors at the distribution transformer are the further best alternative. The shunt capacitor supplies constant reactive power at its location, independent of the load. Thus, optimal compensation given for peak load condition might result in over compensation during light load conditions, necessitating automatic switching schemes.
Fixed capacitors are suitably selected for light load conditions and linked permanently. The automatic switched capacitor bank of rating appropriate for maximum kVA requirement of the concerned distribution system is installed along with essential provision of switching to suit the reactive demand of the system at any particular time. The switched capacitors could be switched off in steps and brought back in service as the reactive load on the system raise.
Q. Let m 1 (t) and m 2 (t) be two message signals, and let u 1 (t) and u 2 (t) be the corresponding modulated versions. (a) When the combined message signal m 1 (t) + m 2 (t) DS
Q. A commercial FMstation broadcasts a signal with 180-kHz bandwidth when |f(t)|max = 2 V. Find kFM for the modulator if the spectral extent of f (t) is 30 kHz, by using Carson's r
the relation between power
A 3 phase 60 hertz induction motor has 8 poles and operates with a slip of .05 for a certain load. Compute in r.p.m. the (a)speed of the rotor with respect to the stator, (b)spe
What are the differences between Colour Graphics Adapter and Video Graphics Array graphics adapters? The Colour Graphics Adapter (CGA), originally also termed as the Colour/G
Q. Motoring mode of rotating machines? The motoring mode has electric power input and mechanical power output. The electromagnetic torque Te drives the machine against the load
AC and DC distribution onboard ships
Connect the 2 kHz (sin ωt) signal to input A of the "Adder" module Connect input B to ground (GND). Connect the outputof the"Adder"(GA+gB) to input A-CH1 of "Scope Selector".
Q. Explain working of Capacitor motors? Capacitor motors have a capacitor in series with the auxiliary winding and come in three varieties: capacitor start, two-value capacitor
Static V- I Characteristics A thyristor works in three basic modes a.Reverse blocking mode b.Forwards blocking mode and c.Forward conducting mode In revers
Get guaranteed satisfaction & time on delivery in every assignment order you paid with us! We ensure premium quality solution document along with free turntin report!
All rights reserved! Copyrights ©2019-2020 ExpertsMind IT Educational Pvt Ltd